Addressable heat detector 920E works with our addressable MN300 panel via a 2-wire bus system
Addressable heat detector 920E works with our addressable MN300 panel via a 2-wire bus system.
The detector realizes real-time acquisition of the heat concentration data and sends back the data to a fire alarm control panel. It can also receive and execute the control commands given by a fire alarm control panel.
The detector is suitable for such industrial and civil buildings that have a great deal of heat when fire takes place, such as kitchens, boiler rooms, generator rooms, drying workshops and smoking rooms and is not suitable for places with a great deal of smoke but little heat.
It can realize electronic coding and rewrite the address via coder.
With a single-chip microcomputer, it can realize real-time data acquisition and processing, realize a curve tracing for the field situation.
It has a temperature compensation function and a sensor fault detection function(fault reporting to fire alarm control panel).
Non-polarity, two-bus connection that ensures convenient installation and maintenance.
Designed with an upper cover and a lower cover and installed on an independent base, it can be installed, debugged and maintained conveniently.
1.Executive standard: GB4716-2005
2.Operating voltage: 24V (pulse modulation)
3.Operating current: <300uA (monitoring status) or<1.5mA (alarm status)
4.Work indication: The red indicator will blink in the monitoring status or remain lit in the alarm status.
5.Weight: about 47g
6.Product class: A2
7.External dimensions: diameter: 100mm, height: 56mm (with the base)
8.Wiring method: non-polarity two-bus system (L1, L2)
9.Operating environment: Indoor, temperature: -10C~+50C; relative humidity: <=95% (40C±2C, without condensation)
10.Coding mode: It can realize electronic coding via coder in situ. Address codes 1 to 324 are available for selection.
11.Installation height: <=8m
12.Protection area: about 60m2. For details, see related provisions in GB50116-98 Code for Design of Automatic Fire Alarm System.
13 Installation and debugging
Determine the location, mounting distance and numbers for mounting the detectors in the protection area according to relevant provisions and regulations of GB50116-98 Code for Design of Automatic Fire Alarm System and GB50166-2007 Code for Installation and Acceptance of Fire Alarm System.
A self-contained complete base is necessary during the installation of a detector. As shown in Fig.5, the model, the external dimensions, the mounting hole diameter and the mounting hole spacing of the base are DZ-910, 100mm×22mm (diameter×thickness), 5mm and 56mm~64mm respectively.
It is proper to use RVS twisted pairs with a section area of equal to or larger than 1.0mm2 for the signal buses L1 and L2.
Specific installation and debugging methods:
1.Make sure the type of the detector matches the type of the host machine of the fire alarm control panel;
2.Use two M4 screws to fix the matched mounting base on the designated position via the mounting holes C and D shown in Fig.5, as instructed in the construction drawing and make sure the matched mounting base has been firmly installed.
3.Use a coder to make the detector coded according to the detector address on the construction drawing.
4.Disconnect the power supply of the fire alarm control panel and connect the detector correctly according to the construction drawing.
5.Place the indicator at position A of the detector (see Fig.1) and position B of the base (see Fig.5), align them with each other, insert the detector into the base and turn the detector clockwise until it is firmly locked.
6.After all the products are installed and checked, connect the power supply of the fire alarm control panel and conduct automatic login.
7.when automatic login is success, the red indicator of the detector will blink once about every 12 seconds, which suggests that the detector has begun to operate normally.
8.Finally conduct an alarm test for the detector through some special tools or direct hot air gun blowing. After the detector gives a fire alarm, the indicator will remain lit and the fire alarm control panel will simultaneously give corresponding alarm prompt information. After the alarm test, reset the fire alarm control panel and restore to the monitoring status.
1.A detector can not share an address with other equipment in a single bus circuit, or else an address conflict may occur.
2.Never dismount the protective cover delivered with the detector too early after the field installation and before the use of the detector, or else the detector may be contaminated.
3.It is not permitted to use open flames (such as lighters) to firing thermistor during alarm tests, so as to avoid damage to the detector. It is recommended to use a hot air gun and other heating equipment in a simulation alarm test.
4.The protection area and quantity of the detectors should comply with relevant provisions in GB50116-98 Code for Design of Automatic Fire Alarm System and GB50166-2007 Code for Installation and Acceptance of Fire Alarm System. .Matched host machine: fire alarm control panel (such as MN300)
- UPC 782123753390
- Brand CST
- Mfg Part # FT-920
Conditions of use
Hello and welcome to Vedard Alarm Systems Store. When you visit or shop at our alarm systems online store, you agree to these conditions.
Vedard Alarm Systems Company attempts to make product descriptions as accurate as possible. However, Vedard does not warrant that product descriptions are complete, current or error-free. If there is any doubts, please feel free to send email to check with us before buying.
Alarm Systems are devices of installation required before using. So, please make sure there is experienced alarm installer, electronic engineer, security service or experienced alarm user for the installation work after item is bought.
Vedard is not responsible for any wrong purchasing, non working of product with wrong configuration. Please make sure the wireless compatibility of buying wireless alarm accessories, wireless sensor with your exist wireless alarm system.
Cause of high rate international shipping charge for you and us, we do not accept fault goods return. But we offer 50% off new one sales for compensation. Product fault evidence is required.
You are welcome to post alarm systems reviews, comments on our website for your purchased products. And you are welcome to leave us a review at third party home security review website at home security reviews
Please make sure the content you posted is accurate, truthful and detailed to help visitors understanding our products and service well. Vedardalarm.com has the right to monitor and edit or remove any activity or content.
Thanks for shopping alarm systems at Vedard Alarm Systems Store.
Preparation for delivery usually takes 3~7 business days.
Generally, DHL shipping service is used for delivery and delivery time is 3~5 business days for most countries.
For package weight less than 2kgs, we may use air post service for delivery and delivery time may be 15~25 days.
Once an order was shipped, you will receive an email with tracking information.
Low customs value will be made to reduce your import tax in our commercial invoice.
If you have special requirement for shipping, please leave comment with us when you place the order. Thank you!
We can send email of alarm system manual for your preparing installing new technology alarm systems. Please contact us to send the alarm system manual.
If your ordered goods is happened out of stock or not available to be shipped, we will issue 100% refund immediately and send email notice to you.
Tracking No. will be provided.
We may use DHL, EMS, China post air mail, Swiss post air mail to deliver your parcel.
The parcel tracking Website is as below:
China post air mail
Swiss post air mail
Your benefit is guaranteed while shopping at Vedard Security Systems Store.
We will refund you product rate once product shipped is found with fault.
But video, photo evidence should be provided and confirmed by our technical department. Refund application should be submitted within 7 days after products received. Refund application should be sent to firstname.lastname@example.org and title with Refund order #.
Buyers are requested to read and know product carefully before buying. And you can ask question via our forum or e-mail. We don't accept wrong buying refund.
Buyer can select to return to us with product rate and freight rate refund. But return cost is charged by buyer.
Household alarms should be as necessary as household appliances. But home alarms are special products.It plays an important role in keeping the family safe.Therefore, the installation and use of family alarm should be based on the home environment safety needs and alarm installation requirements. For wireless alarm, different manufacturers, different brands of alarm equipment is not compatible. Therefore, before buying an alarm, carefully read the product description and understand the brand of the product to determine its wireless compatibility.
There are many kinds of alarms. Alarm manufacturers designed a variety of alarms for different users of different habits or environmental differences. Therefore, you can choose the most appropriate alarm according to your own security needs.
Before buying alarm equipment, you should understand the functions and characteristics of all kinds of alarms and your own security needs. If you have any questions, please contact the product seller. Professional alarm equipment sales will provide detailed product installation instructions, video demonstrations, and technical guidance.
The products details and technical support for vedardalarm security can be found at https://www.vedard.com/forum